CONDENSER REPLACEMENT - CONTINUED
CLEANING AND INSPECTION
Clean and inspect all parts IAW General Maintenance Instructions (WP 0014 00).
A/C condenser weighs approximately 40 lb (18 kg). Use extreme caution when handling heavy parts. Pro-
vide adequate support and use assistance during procedure. Failure to follow this warning may cause injury
Install condenser (1), four washers (3), and new locknuts (2) on four mounting studs (4).
Use caution when using adhesives and sealants. Prolonged inhalation of vapors can cause lung irritation.
Contact with skin can cause dermatitis. Wear gloves and safety goggles and use product in a well-ventilated
area away from open flame. If ingested, keep individual calm and seek medical attention. DO NOT induce
vomiting. If contact with skin or eyes is made, flush thoroughly with water. Dispose of cleanup rags IAW
local policy and ordinances. Failure to follow this warning may cause injury to personnel.
Install wires and hoses as tagged during removal.
Apply refrigerant oil to new O-ring and install A/C hose (6) on condenser (1).
Apply refrigerant oil to new O-ring and install A/C hose (5) on condenser (1).
END OF WORK PACKAGE
0018 00-3/(0018 00-4 Blank)